In recent years the Separations Research Program (SRP) at the University of Texas at Austin has been involved in testing pilot plant processes that require significant equipment modifications and additions. In these activities, process setup and decommissioning take about three times longer than the actual runs. So, decreasing setup time and pilot plant downtime are a high priority. Use of wireless transmitters provides a new degree of flexibility in reconfiguring the process without installing or relocating transmitter wiring.
The flexibility of being able to work on the absorber and stripper without disconnecting cables offers ongoing benefit by reducing downtime and maintenance. However, many measurements that are candidates for switching to wireless transmitters serve for control. Thus, measurement reliability and control performance achievable using wireless transmitters were of primary concern. To allow direct comparison of the performance of wireless versus wired installations, wireless transmitters were installed in parallel with wired transmitters for a few critical loops on an absorber and stripper process. This article presents the results of these tests.
The equipment setup used to evaluate application of wireless transmitters in control currently serves for testing new energy-efficient stripping processes associated with carbon dioxide capture from coal-fired power plants. From a process standpoint, this involves an absorber to remove CO2 from a simulated stack-gas stream using an amine-based solvent and then a stripper to recover the CO2 and recycle the regenerated amine solution to the absorber. The photo shows the equipment.
The absorber generally tests proprietary solvents and packing or tray internals. The absorption column provides two 10-ft beds of packing. A liquid collector and liquid re-distributor are located in the middle of the column. In the SRP CO2-capture experiments, ambient air is blended with recycled stripped CO2 and make-up CO2 and fed to the bottom of the column. Carbon dioxide is absorbed into the downflowing amine solvent as the gas flows up through the packing. The exiting solvent, referred to as the rich amine, goes to the stripping section to remove the absorbed CO2.
The stripper tests packings and determines the energy efficiency associated with a proprietary solvent. This column also has two 10-ft beds of packing. A liquid collector and liquid re-distributor are located in the middle of the column. The solvent leaving the absorber, referred to as the rich amine, is heated with the stripper bottoms liquid using a cross-plate exchanger and then is fed to the top of the stripper. A kettle-type reboiler generates vapor to strip off some of the carbon dioxide. The overhead from the stripper goes to a shell-and-tube condenser where the vapor is condensed and lean amine is returned to the absorber feed tank.
Over the last few years development and design of wireless field devices for the process industries has rapidly advanced. After a review of available wireless technology, WirelessHART devices were selected for installation at the SRP. (For details about the technology, see "Make the Most of WirelessHART.") Pressure and differential pressure transmitters were put in to support testing of control of column pressure and steam flow.
The WirelessHART gateway was centrally located in the process area and connected to the control system via Ethernet. A DeltaV control system installed in the SRP provides standard support for the WirelessHART gateway as well as configuration, setup and diagnostics of WirelessHART devices. Thus, the effort to integrate these devices into the control system software configuration matched that associated with traditional field devices. Because these devices are battery powered, no power wiring was required to install them in the process.