In some projects, condensate is being recovered from LP steam headers and utility stations using steam traps. (This condensate is collected in condensate pot and reused as boiler feed water.) But this condensate recovery is done only for steam headers and utility stations located at 4.8m lvl from grade or higher. This is not done for utility stations at grade lvl. The condensate from the same is just thrown out. What is the reason or base to decide the 4.8 m level?
Have an insight or suggestion?
Login or register to post a comment.
Veerasamy Venkatesan Forum Moderator 13 Posts
Re: Reusing Condensate as Boiler Feed Water24 November 2008 at 1:29pmCondensate from any level could be collected and reused as boiler feed water, as long is its quality meets the boiler feed water specs.
In this case, the available lower head pressure of the condensate may not be enough to get into the existing return pipe line or into the condensate pot and hence would start accumulating at the source itself.
By modifying the return pipeline and lowering the receiver pressure, the condensate from below 4.8M level condensate sources also could be collected and pumped back to use as boiler feed water.
samlucas cas Community Member 1 Post
Re: Reusing Condensate as Boiler Feed Water14 June 2013 at 2:30am Last edited: 14 June 2013 at 3:04amThere are many different types of boiler systems on the market today. From heat recovery boilers and solid fuel boilers to watertube boilers, they all serve their own unique purpose. Watertube boilers come in different types and are typically used as an energy source when an emergency or any other occasion strikes. A water tube boiler usually comes as a longitudinal drum boiler, cross drum boiler or bent tube (Stirling boiler). Read on for the ways in which these boiler systems differ. Cheap Boilers