When installing a vertical pump, should the eccentric reducer on the discharge side of the pump be installed with the flat side on top?
Have an insight or suggestion?
Login or register to post a comment.
Ross Mackay Forum Moderator 93 Posts
Re: Vertical pump installation27 August 2007 at 1:29pmUnder no circumstances should there be an eccentric reducer on the discharge nozzle of a pump, vertical or otherwise. A pump discharge, vertical or horizontal, should be fitted with a concentric increaser.