There should not be a reducer at the discharge. The reducer should be on the suction and reducing the system pipe size down to the size of the pump flange. If the pump suction is horizontal, then the reducer should be an eccentric reducer with the flat side on top.
Have an insight or suggestion?
Login or register to post a comment.