I have a pump motor start 660 run 380 volts and power supply is 380 and control for 380. If I purchase a new pump motor 380 start run 220 volts in panel there is timer and two contactor how can I connect new motor to same old motor connection?
Have an insight or suggestion?
Login or register to post a comment.
Tom Bishop, P.E. Forum Moderator 17 Posts
Re: How can I connect a new motor to same old motor connection?8 July 2009 at 1:29pmAs I interpret this inquiry the motors are probably wye-start delta-run, with one being 380 volts delta-run and the other 220 volts delta-run. If the new motor is rated 380 wye and 220 delta, it will need to be reconnected or rewound for use at 380 volts delta-run.
The 220 delta 380 wye connection motor can be used as a 380 wye across the line start motor. The winding would not be changed. However, the application must be able to withstand the increased (by 300%) torque of the across the line versus wye-delta start mode. Also, the starter must be capable of the current associated with across the line starting. The wye delta starter is not reconnectable for across the line starting due to the higher (by 300%) starting currents.