For an effluent having approximately 500 ppm chlorides, can we use a pump made of 316 stainless steel?
Have an insight or suggestion?
Login or register to post a comment.
Brian Dalder Forum Moderator 177 Posts
Re: Can we use a 316SS pump?6 September 2011 at 1:29pmAccording to ASM Handbook Vol. 13B (Corrosion: Materials), the recommended maximum chloride level for 316/316L alloys in water systems at ambient temperature is 1000 ppm. However, the suitability of 316 stainless steel in your application will depend not just on the level of chlorides, but what other constituents are present and at what levels, what the normal and maximum operating temperatures are, the degree of aeration, etc.