In one boiler we use a stainless steel 309 belt to keep the U-tube in a linear position. The SS 309 is exposed to 1134 ppm sulfur dioxide at 700-800 degrees C continually. Do I need to consider any corrosion allowance in the design or change the material?
Have an insight or suggestion?
Login or register to post a comment.
Brian Dalder Forum Moderator 169 Posts
Re: Do I need to consider corrosion allowance for austenitic stainless steels?25 May 2010 at 1:29pmHigh chromium grades of austenitic stainless steels (e.g., 309 and 310) are used in oxidizing environments and high temperatures. According to ASM Specialty Handbook on Stainless Steels, it is difficult to generalize corrosion rates in flue and process gas environments because gas composition and temperature may vary considerably within the same process unit. Combustion gases normally contain sulfur compounds; sulfur dioxide is present as an oxidizing gas along with carbon dioxide, nitrogen, carbon monoxide, and excess oxygen. The resistance of stainless steels to normal combustion gases increases as the chromium content increases. SS 309 has one of the highest chromium contents (22-24%) in the austenitic family and has been successfully used in combustion gas environments. Whether 309 will work in your case, depends on the specifics of the environment. As an aside, corrosion allowances are not generally useful for austenitic stainless steels since they tend to experience localized corrosion.