The silicomolybdate test measures soluble (reactive) silica. It does not measure colloidal silica. It is worth noting that reactive silica does not refer to only monomeric silica (silicate ion). It also includes other oligomeric species such as dimers, trimers, tetramers, etc.
For all practical purposes, the silicomolybdate test offers a good indication of the soluble silica in the system. However, occasional measurements of total silica ," i.e., soluble and colloidal ," are recommended to ensure no silica is lost to precipitation and deposition. These measurements require sample treatment or elaborate instruments and techniques (e.g., inductively coupled plasma atomic emission or atomic absorption spectroscopy) and are not practiced routinely in the field. Samples usually are sent to an independent laboratory for study.
Silica is an undesirable scale for several reasons. It severely impedes heat transfer. It is tenacious and costly (and potentially hazardous) to remove. It is extremely prone to co-precipitation with other scales, particularly iron (hydr)oxides. It is often the limiting factor for limiting high cycles of concentration.
The amorphous character of silica deposits precludes the use of conventional crystal modification technologies. Molecules such as phosphonates that are effective mineral-scale threshold inhibitors provide virtually no benefit for silica-scale inhibition. They provide only an indirect benefit by maintaining a cooling tower free of other deposits that can act as precipitation nuclei for silica or catalyze silica precipitation in the bulk.
Just like the Gordian Knot ," the difficult, intractable and often insolvable problem ," resolution of the silica problem might require nonconventional means. Several factors, unique to the individual system, must be taken into consideration. These factors include water chemistry (presence of other scaling ions), nature of the silica (colloidal and/or reactive) in the make-up water, target cycles of concentration (need for water conservation), feasibility of mechanical silica removal (filtration and softening), capital costs (for chemicals and/or equipment) and many others. Careful selection of a general scale treatment program, combined with a silica-scale inhibitor and/or dispersant, is a good starting point for attaining a silica deposit-free cooling water system.
1. American Public Health Association, Standard Methods for the Examination of Water and Wastewater, 19th Ed., 1995, pp. 4,"18.
2. Andersson, K.R. et al. Soluble Silicates, American Chemical Society (ACS) Symposium Series, 1982, p. 115.
3. Bergna, H.E. The Colloidal Chemistry of Silica, ACS Symposium Series, 1994, p. 1.
4. Bremere, I. et al. Proceedings of the Conference on Membranes in Drinking and Industrial Water Production, Vol. 2, 2000, p. 129.
5. Chan, S.H. et al. Journal of Heat Transfer, Vol. 117, 1995, p. 323.
6. Daniels, D. Power, September 2002, p. 43.
7. Dubin, L. Surface Reactive Peptides and Polymers, ACS Symposium Series, 1991, p. 354.
8. Gallup, D.L. Geothermal Resources Council Transactions, Vol. 21, 1997, p. 49.
9. Gill, J.S. Materials Performance, Vol. 37, November 1998, p. 41.
10. Hann, W.M. et al. 1993 International Water Conference Proceedings, Paper 59, p. 358.
11. Harfst, W. Ultrapure Water, April 1992, p. 59.
12. Hayakawa, S. et al. Journal of the American Ceramic Society, Vol. 82, 1999, p. 2155.
13. Henley, M. Ultrapure Water, December 1992, p. 13.
14. Hennis, S. et al. Chemical Processing, Vol. 64, June 2001, p. 32.
15. Iler, R.K. The Chemistry of Silica, Wiley-Interscience, New York, 1979.
16. Kristmannsdottir, H. et al. Geothermics, Vol. 18, 1989, p. 191.
17. Masarwa, A. et al. Desalination, Vol. 113, 1997, p. 73.
18. Midkiff, W.S. and H.P. Foyt. Materials Performance, February 1978, p. 17.
19. Radzig, V.A. Colloids and Surfaces: Physicochemical and Engineering Aspects, Vol. 74, 1993, p. 91.
20. Reay, P.F. and W.D. Bennett. Analytica Chimica Acta, Vol. 198, 1987, p. 145.
21. Schenk, J.E. and W.J. Weber Jr. Journal of the American Water Works Association, February 1968, p. 199.
22. Smith, C.W. Industrial Water Treatment July/August 1993, p. 20.
23. Tatterson, G. Chemical Processing, Vol. 65, January 2002, p. 12.
24. Weres, O., A. Yee and L. Tsao. Journal of Colloid and Interface Science, Vol. 84, 1981, p. 379.
25. Wibowo, J. et al. Semiconductor Pure Water and Chemicals Conference Proceedings, 1997, p. 43.
Demadis is an assistant professor of chemistry at the University of Crete in Greece. He has extensive experience in chemical water treatment research and development and also in technical and field support. Contact him +3 2810 393651, or via e-mail at email@example.com.